ESP Downhole Power Quality - Do We have a Healthy Cardiovascular System?
- A. J. Sandy Williams (Artificial Lift Performance Ltd) | David Shipp (Capstone Power Systems Engineering)
- Document ID
- Society of Petroleum Engineers
- SPE Gulf Coast Section Electric Submersible Pumps Symposium, 13-17 May, The Woodlands, Texas, USA
- Publication Date
- Document Type
- Conference Paper
- 2019. Society of Petroleum Engineers
- Quality, ESP, Power, Specification, Downhole
- 13 in the last 30 days
- 157 since 2007
- Show more detail
- View rights & permissions
|SPE Member Price:||USD 8.50|
|SPE Non-Member Price:||USD 25.00|
Electricity is the lifeblood of the Electric Submersible Pump (ESP), the Variable Frequency Drive (VFD) is the heart that keeps it going, the power cable is the artery that provides the blood and the motor is the equivalent of the body that moves. As Doctors, if we looked at our system "would we pass our annual physical exam"? Surprisingly, there is no specification in our industry for the ‘blood’ or electricity we provide to our ESPs, a shocking (pun intended) omission when most operators desire increased ESP runlife. This paper will identify the key aspects (what and why) of healthy power going downhole and put forward a proposed specification.
In the 2017 ESP Symposium a breakout session was run that looked at downhole power quality (PQ) and posed the question "Is our operating environment worse than other industries and do we apply the best practices from other industries?". The short answer was that our operating environment is extremely challenging and that we have not adopted the learnings that other industries have applied. As part of the breakout, these key learnings were presented. There was overwhelming agreement in the room that a downhole PQ specification is required. Volunteers were solicited to work on a committee to put together such a specification.
This paper will illustrate the best practices from other industries and put forward the rationale and a practical methodology for applying PQ best practices to ESPs. The key aspects of PQ will be presented in layman's terms so that this work can be easily understood by petroleum engineers using ESPs.
Many of the PQ improvements can be implemented retroactively at surface and can provide benefit to existing ESPs as well as provide a basis for technical requirements as part of the surface and downhole specification for new wells. The consequences of poor power quality are ESP component failures (penetrator, cable, splice, MLE / pothead, motor end turn, motor bearing, sensor, shafts) and short runlives. This paper will put the information and practices in the hands of the operator to act to improve ESP runlife.
|File Size||2 MB||Number of Pages||31|
Vance, J. M., Palazzolo, A. B., & Zeidan, F. Y. (1987). Electric Shaft Currents in Turbomachinery. 16th Turbomachinery Symposium. Texas A&M University. https://oaktrust.library.tamu.edu/handle/1969.1/163618
Manz, Lester B., Morgan, Robert B. Mar 01, 1999 Mating New Variable Frequency Drives to Existing Motors https://www.ecmweb.com/design/mating-new-variable-frequency-drives-existing-motors
Kluck, Jim. Best Practices for Trouble Free VFD Operation https://www.flowcontrolnetwork.com/best-practices-for-trouble-free-vfd-operation/
Marchi, Jay. Best Practices for VFD Grounding: Minimize the damage caused by common mode noise. Pumps & Systems http://www.pumpsandsystems.com/print/pumps/january-2016-best-practices-vfd-grounding
Schuerger, Robert. Overview of Grounding for Industrial and Commercial Power Systems. March 26, 2010, San Francisco IEEE/IAS Chapter Seminar http://ewh.ieee.org/r6/san_francisco/ias/archive/pdf/2010ShortCourse/Overview_of_Grounding_for_Industrial_and_Commercial_Power_Systems_Schuerger_HP_Mar_2010.pdf
Shipp, David. All About Sinewave Filters (2013) Eaton Technical Education Conference https://www.youtube.com/watch?v=rzErmKoajQw
Cheng, JohnDr IEEE Standard 519-2014 Compliance, Updates Solutions and Case Studies. Schneider Electric. http://www.egr.unlv.edu/~eebag/IEEE_STD_519_1992vs2014.pdf